I found this boiler without a start command. I enabled the boiler to run and found the flow switch would not close, and the pressure relief would not operate. I removed the flow switch and pressure relief and cleaned them. The boiler fired and I had to adjust the bypass to keep my inlet temp above 130°. I will return to replace the pressure relief and a couple leaking gaskets on the victaulic fittings. Thanks for watching.