To see the boiler after the repair click links:
To read more videos about this boiler repair work see well below
Emergency Boiler Repairs London & Gas Safe Registered Gas Engineers London.
emergency call out boiler breakdown repairs London. All plumbing, gas boiler and central heating repairs carried out!!
emergency gas boiler repair London. Specialists on domestic gas boilers, appliances and central heating system repairs in London. We carry a large selection of spare parts as van stock and have local engineers all over London. We'll put the heat back into your home . . . FAST!
Some of the services we provide:
Emergency Boiler Repair London
Emergency call out Boiler Repairs
All Gas Breakdown Repairs
Combi Boiler Repair London
Full Central Heating System Repairs
Hot Water Repairs
Fans, PCB, Pressure Switches, Gas Valves & Controls
Pipework, Radiators, Cylinders, Pumps and Valves
Fault Finding & Diagnosis
Servicing and Maintenance
Landlord's Gas Safety Certificates CP12
This Video was taken during the testing of the boiler after parts are replaced, namely Fan & Gas valve.
this boiler was Classified as at risk by British Gas due to :
1. Fan not working
2. Gas valve not working
3.. External pump not working
Once I done further checks about the fan - APS - PCB - it was found that the 240 power is percent at the fan during the ignition sequence. Also during the dry test ( with Gas Off) it was noticed that the power to the gas valve is percent and I can hear a good clicking sound of the fan proving the valve is opening and closing.
I just replaced the Fan and open the capped gas meter - uncapped it and done a tightness check - guess what - 6mbar pressure drop on U6 meter ( this is ID by GSIUR) - shut the boiler gas isolator - retested it no pressure loss. Replaced the gas valve, replaced the pump everything is working.
BG should have ID the boiler and written about the gas leak - but instead they AR it and told the owner that they need to replace it at extra cost. ( this is probably why Advertising board banned their advert - Look After your world advert)
Need to recommission the boiler - cleaned the burner ( this property was closed for nearly a year and the owner just bought it) adjusted the burner pressure to match with the boiler size, gas rated it - still there is a yellow tip on the flame. Done a combustion analysis - more that satisfactory.
It took a while for the yellow tip on the flame to diminish, I believe its the dirt and dust burning after this boiler was not used for a long time.
When I classified a boiler at risk I give clear details of why - in this case the British Gas Engineer should have written it : Gas valve letting by 6mbar in 2 min., not telling the owner that the boiler need to be replaced and walk away,. That's what they have done. They have classified boiler at risk and gave a list of parts to be replaced and told the owner that they need a new boiler.
BG should have ID the boiler and written about the gas leak - but instead they AR it and told the owner that they need to replace it at extra cost. ( this is probably why Advertising board banned their advert - Look After your world advert it should be re-advertised as Look After BG Profits)
The boiler was repaired, and I am writing this after 3 months. Last week the owner called me telling that the heating in not coming on. when I checked it - the Honeywell room thermostat has gone out of calibration. It never make the switch live until the dial is at 30C regardless of the room temperature.
To see more videos about this boiler repair from the start - click following links:
If you live in London within M25 and need a boiler service, Property Management Service, or other plumbing or electrical service, Go to our website and checkout the charges and book us by calling 02082008580 / 07974711639, or email firstname.lastname@example.org . Please visit our Website www.unicuk.com to see our other services.